hi, i recently had my boiler replced, an engineer came out after a year, to reservice it a month ago!!now it has shut off completely..i am getting "SER-2088-No1-time etc. it beeped for a while now i cant use it
Page 5 of your instruction book says:
"The FP715 Si is fitted with an installer service interval timer ... Setting instructions for this gas safety feature are only available to bona fide heating installers".
It's designed as a feature for landlords, to ensure that their tenants get their boilers serviced regularly. It limits the boiler operation until the service is done
Your 'engineer' should have reset the service timer when he did the service - get him back to do it, for free! If he doesn't know how, he's a cowboy. He needs to ask Danfoss for the instructions. If he objects, threaten him with your local Trading Standards office - he didn't do the job properly.
repairs can be dangerous.
In many instances work should only be undertaken by a qualified
professional. Ensure you have read our Small
Print page before using information supplied via this website.